Buy B DANFOSS REFRIGERATION EKC D1, ller, I-pack the best price, fast worldwide shipping, up to 65% discount DANFOSS. EKC controllers can be used for a wide range of different refrigeration applications .. Regolatore per il controllo della temperatura – EKC D1, Literature. I need some help on this danfoss EKC D1. Its controlling a small freezer unit The set-point temperature is º The R1 seting is diferential is.
|Published (Last):||1 January 2017|
|PDF File Size:||16.21 Mb|
|ePub File Size:||15.57 Mb|
|Price:||Free* [*Free Regsitration Required]|
Defrost on demand 1 Based on refrigeration time When the aggregate refrigeration time has passed a fixed time, a defrost will be started. This function requires the use of both an S3 and S4 sensor. S3, S4 or a combination of the two. Go to About section Our Engineering. Defrost start, hour setting Defrost start, minute setting 1 and 11 belong together, etc.
All settings except for Application o61 and Address o03 will be copied. These settings can only be made when a data communication module has been mounted in the controller and the installation of the data communication cable has been finished.
Controller for temperature control – EKC 202D1 Manual
System Management Electronic Controls: Order number or SW version do not match 9: Weighting is set in A Here are the messages that may appear: Here you ekx set the point at which the high temperature alarm is activated. I copy the parameters from other controller to this one, but noting has change. Copying still going on The information can be found in o65 or o66 a couple of seconds after copying has been started.
The controlling unit is the controller with a defrost diagram installed in t1-t6, tt Access code 2 partly access Save the controllers present settings to the programming key.
See the functions in settings o02 and o The next change will follow the planned diagram. An A alarm will not be visible as long as 202d is an active E alarm. This function can only work in 1: There is stop based on time -d-: The battery module is used in conjunction with the real-time clock and will keep the clock going during lengthy power failures.
Electronic Controls: Evaporator Controls with Thermostatic Expansion Valves
After two seconds you can move into the menu again and check whether the copying was satisfactory. When the thermostat calls for refrigeration will the compressor relay be 202d11.
Here a combination of S3 and S4 is used. The function is not active during a defrost or start-up after a defrost. A03 and A12 are to be used for time delay. Now, when I am officialy citizen off EU, 202d am looking for decent job! Night time cover placed over Night appliance time cover detected Night time cover removed Removal of night time cover detected Example of temperature sequence Example of settings: Danfoss EKC D1 temperature settings The sensor is correct, i change the other controller whit other kec and the problem goes with the controller I went to the store and got a new one and the problem is solved.
Controller for temperature control – EKC D1 Manual |
The set value can emc locked or limited to a range with the settings in r02 and r Go to procurement section Procurement. Go to career section Working at Danfoss. Regulator til temperaturstyring – EKC D1.
C30 set to on so relay acts inversely? Four relays will cut the required functions in and out — the application determines which. Alarm delay Time delay for door alarm The time delay is set in minutes.
Electronic Controls: Evaporator Controls with Thermostatic Expansion Valves – Documents
The value is the same as the one set for night setback, but will only be raised if the value is positive. The controller will register when the DI input is activated. Here you set which of the 3 applications is required. The few selected settings will now be transferred to the menu. Defrost on demand — S5 temperature The controller will follow the effectivity of the evaporator, and via internal calculations and measurements of the S5 temperature it will be able to start a defrost when the variation of the S5 temperature becomes larger than required.
The buttons When you want to change a setting, the upper and the lower buttons will give you a higher or lower wkc depending on the eekc you elc pushing. Only the function belonging to the selected application is shown.
Push the upper or the lower button and find that parameter you want to change 3.