Beiblatt Zum Dvgw-Arbeitsblatt G Gas-Druckregelanlagen Fuer Eingangsdruecke Bis Einschliesslich Bar; Planung, Fertigung, Errichtung. within the DVGW Gas Innovation Campaign which includes additional tests .. [ 10] DVGW, Hrsg., Technische Regel Arbeitsblatt DVGW G (A) Juli Insbesondere sind die DVGW-Arbeitsblätter G , G und G zu beachten. Umbau, Ersatzteile. Jegliche technische Veränderung ist untersagt.
|Published (Last):||25 September 2013|
|PDF File Size:||19.45 Mb|
|ePub File Size:||16.2 Mb|
|Price:||Free* [*Free Regsitration Required]|
Application deemed withdrawn, or ip right lapsed, due to non-payment of renewal fee. The Reversierungs-line system is technically complex, because of the large number of components and thus cost-intensive and requires a large spatial extent of the GPRM system.
If f test pressure of considerably more than 6 bar is applied and all or all parts of the piping or facility under test have not been tested beforehand at the same test pressure or at a higher test pressure, special safety precautions shall be taken e.
Piston Pressure Gauges B 3. The sequence in method B2 is depicted schematically in Fig. Connection interface for connecting arbeitsblayt treatment system at arneitsblatt of e. This automatically closes when an inadmissible pressure difference occurs. In order to minimise fluctuations in temperature during the test period, the pipe trench shall be backfilled as far as possible. Air may also be replaced by other suitable gaseous media; below, reference is only made to air.
Bei den Messeinrichtungen The measuring devices 6a 6a. Die Filter the filters 10a 10a. In particular, the following aspects should be taken into consideration: The system is also easy to maintain.
Only the volume of water which is drained off last and the associated reduction in pressure shall be taken into consideration for purposes of evaluation. This evens out the flow, thereby reducing measurement errors and damps disturbing sound. The measuring devices concerns advantageously ultrasonic flowmeters or Coriolis mass flowmeters. A preferred embodiment is characterized in that two measuring devices are serially integrated into the wiring harness.
Air processing system esp. Stop valve for terminal of water treatment apparatus at pipe line, has inlet and outlet, where water treatment apparatus is connectable between inlet and outlet.
DVGW G 469 English
The change in arbeitslatt of the test section can be established from the following equation: Playing pressure losses a minor role, at least one flow rectifier between the systems for measuring the flow rate can be located in order to optimize the flow calming arbeitsnlatt. The object of the invention accordingly is to provide a GPRM plant for bidirectional operation, which requires little technical effort and their footprint is small. By advantageous embodiments undue repercussions between control and measurement devices be prevented while minimizing the pressure drop across the system.
DE DEU1 en Master pressure gauges category min.
Typical instruments are iris, displacement, turbine, ultrasonic and eddy gas meters. The gas pressure arbeitdblatt according to the invention and -messanlage GPRM plantin particular for high-pressure area, is compact and requires little space.
Due to the linear wrbeitsblatt of atypical vibrations are avoided. Are equipped with butterfly valves in wafer. Is upstream or downstream. In the opposite direction of inflow her measurement error is well above the approved by the Eichordnung values. This allows the addition of further routes to increase the transport capacity.
Im Falle gleicher Srbeitsblatt der Leitungsnetze In the case of identical design pressure stages of the pipeline networks 3 3. The relevant sections about testing methods B1, B2, B3 and C3 refer to other necessary measurement devices and their respective requirements.
Gas-Druckregelgerät RMG |
Der Betriebs-Leitungsstrang The operating line strand 1 1 dvgs der Reserve-Leitungsstrang and the reserve-wiring harness 2 2 sind einerseits an ein erstes Leitungsnetz on the one hand to a first line network 3 3 und andererseits an ein zweites Leitungsnetz and on the other hand to a second transmission system 4 4 angebunden.
In the event of testing during periods arbditsblatt which the risk of frost may be encountered, exposed arbeitsblatr sections shall be protected against freezing. Measurement accuracy shall be increased for volumes of more than 3,m. The actual pressure test shall only be started when the temperature of the testing medium has been allowed to adjust to the temperature of the surrounding soil or ambient atmosphere.
In legal metrology in the gas high-pressure area currently time series circuits in particular turbine and ultrasonic flowmeters are used.
DVGW List – @ 제품시험 / 인증대행@-ASTM, BS, MIL, DIN, EN, Automotive 규격시험
Water may also be replaced by other suitable liquid media; below, reference is only made to water. By adhering to the claimed range limits in the positioning of the measuring devices with each other and adherence of the claimed spacings of the measuring devices to the upstream flow straighteners is the bi-directional operation with minimal pressure losses possible.
See pressure testing methods B1 or B2 with respect to checking for absence of air. After reducing the pressure to a value as low as possible hold time 30 minuteswhich should be at least 2 bar at the absolute highest point along the pipeline, and after increasing the pressure to the test pressure, the pressure shall again be held for at least 90 minutes. For this purpose, the pressure shall be reduced at least twice. Table of Contents51 Scope2 General Usually GPRM plants for the unidirectional operation are provided, ie, the gas pressure regulator and the gas-measuring device are only flows from one direction.
It is a GPRM plant for natural gas in the high pressure area in the course of trade. Sound-absorbing technical devices would lead to increased pressure losses that affect the line capacitance sensitive. EvaluationDue to the measurement tolerances of this method, changes in volume generally result which, in total, do not cancel each other out and which can be converted by inserting all the tolerances into the relevant calculation formulae.
For the purpose of determining this permitted hourly change in volume, it is therefore sufficient to apply the following simplified formula: An beiden Enden des Betriebs-Leitungsstranges At both ends of the operation wire bundle 1 1 befinden sich Absperreinrichtungen are shut-off devices 5a 5a.
By this structure repercussions from the control system are minimized to the measuring device. According to a further feature of the invention the measuring device is at least one upstream or downstream flow straightener. The GPRM plant is built in a standardized and modular train construction. Pure-water supply system – has insert in ring main reducing pressure with pipe connected. The GPRM system includes a measuring device arbeitsblxtt measuring the flow.